Raychem HIQ mineral insulated (MI) Inconel 600 series heating cables are suited for use in hazardous areas. The Inconel 600 sheath offers excellent corrosive properties against a wide range of organic acids and alkalis, as well as chloride stress-corrosion cracking, in combination with a high temperature withstand capability.
HIQ cables are typically used in bitumen plants, gas plants, oil reﬁneries, reactors and vessels, sodium loops and a wide variety of other heat-tracing applications where temperature resistance, power output and durability are required and exceed the limitations of stainless steel sheathed MI heating cables.
The heating cables can be used for exposure temperatures up to 700°C and a typical power output up to 300 W/m. Higher temperatures and power outputs can be achieved, contact Pentair for assistance. The heating cables are offered as bulk cables as well as factory-terminated heating units employing brazing or laser welding techniques to ensure optimum quality of the connections.
The offering is completed with a full range of components for installation, connection and splicing of the heating cables.
System (Heating Units):
|Order Reference||Nominal Resistance
[Ω/km @ 20°C]
[x 10-3 /K]
|Max Coil Length
Brass glands are standard on all heating units. Other materials are possible, contact Pentair for more information. Delivery length of bulk cable on coil depends on type of resistance and is limited by max. coil length as indicated in the table on top.
Factory terminated elements are limited by a max. weight of 50kg, however to ensure practical and safe on-site handling, it is strongly recommended to limit element lengths to 25 - 30kg. Not all resistances are standard items and as such may not be in stock. Contact Pentair to conﬁrm lead time. Pentair requires the use of a 30 mA residual current device to provide maximum safety and protection from ﬁre.
Where design results in higher leakage current, the preferred trip level for adjustable devices is 30 mA above any inherent capacitive leakage characteristic of the heater as speciﬁed by the trace heater supplier or alternatively, the next common available trip level for non adjustable devices, with a maximum of 300 mA. All safety aspects need to be proven.
Also refer to the components section for more details on heating units, accessories and nomenclatures.
|Cable Sheath Material||Inconel 600|
|Earth Leakage||3 mA/100m (Nominal at 20°C)|
|Max Exposure Temp||450°C (Brazed Heating Units)|
|Max Exposure Temp||700°C (Heating Cables)|
|Max Exposure Temp||700°C (Laser Welded Heating Units)|
|Min Bending Radius||6 x outer diameter at -60°C|
|Min Cable Spacing||25mm for hazardous Areas|
|Min. installation temperature||-60°C|
We make every effort in answering your questions. Below is a list of those questions we are frequently asked. Click on a question to expand its answer.
Self limiting / self regulating heating tape adjusts heat output to equal the heat loss from the pipe work. As pipe temperature falls the electrical conductivity of the semi-conductive core increas...
Yes, utilising our in-house design facilities, we can design your complete trace heating requirement.
Yes, when using trace heating on plastic pipes ensure that ATE- 180 aluminium tape is used to help disperse the heat around the pipe.
Yes, thermal insulation is required on all heat trace applications. Without insulation, surface heat losses can increase approximately 4-5 times.
Most applications can simply be straight traced, reducing costs of materials and installation time without compromising on operational requirements.
If the surface area of the pump is substantially greater than that of the adjoining pipework then extra heating cable may need to be considered (depending on wattage of cable installed). Pumps and ...
Generally, no maintenance of our trace heating systems is required but it is recommended that the system is checked for operational and electrical integrity periodically or prior to the winter or p...
System checks depend on the system installed, constant wattage systems can be fully checked for insulation resistance and continuity. Self regulating systems can only be checked for insulation resi...
This is used for a pipe freeze protection application. Electric heat tracing, heat tape or surface heating, is a system used to maintain or raise the temperature of pipes and vessels. Trace heat...