|Variant||-5 deg C to +15 deg C|
AT-TS thermostats provide temperature control in a safe area. The temperature set point can be checked through a window in the lid. LED's indicate when cables are energised (Heating on) or when the temperature sensor is defect (sensor break or sensor short circuit). The temperature sensor has a length of 3 meters and can be shortened for ambient sensing operating. Direct connection of the heating cable is possible (Connection kits need to be ordered separately).
Line sensing control thermostat with an adjustable temperature range between 5 Deg C to +15 Deg C. The Raychem AT-TS-13 thermostat is ideal for temperature maintenance on pipelines for fatty waste water.
|Max. switching current||16amp 250VAC|
Raychem SB-101 Support Bracket for Junction Box/Thermostats
Quick Find: 478, Part Number: 990944-000
£29.36 inc VAT
Raychem SB-100 Support Bracket for Junction Box/Thermostats
Quick Find: 477, Part Number: 192932-000
£36.85 inc VAT
Raychem SB-110 Support Bracket for AT-TS-13, AT-TS-14 and JB16-02
Quick Find: 479, Part Number: 707366-000
£18.84 inc VAT
We make every effort in answering your questions. Below is a list of those questions we are frequently asked. Click on a question to expand its answer.
Self limiting / self regulating heating tape adjusts heat output to equal the heat loss from the pipe work. As pipe temperature falls the electrical conductivity of the semi-conductive core increas...
Yes, utilising our in-house design facilities, we can design your complete trace heating requirement.
Yes, when using trace heating on plastic pipes ensure that ATE- 180 aluminium tape is used to help disperse the heat around the pipe.
Yes, thermal insulation is required on all heat trace applications. Without insulation, surface heat losses can increase approximately 4-5 times.
Most applications can simply be straight traced, reducing costs of materials and installation time without compromising on operational requirements.
If the surface area of the pump is substantially greater than that of the adjoining pipework then extra heating cable may need to be considered (depending on wattage of cable installed). Pumps and ...
Generally, no maintenance of our trace heating systems is required but it is recommended that the system is checked for operational and electrical integrity periodically or prior to the winter or p...
System checks depend on the system installed, constant wattage systems can be fully checked for insulation resistance and continuity. Self regulating systems can only be checked for insulation resi...
This is used for a pipe freeze protection application. Electric heat tracing, heat tape or surface heating, is a system used to maintain or raise the temperature of pipes and vessels. Trace heat...