Raychem 20KTV2-CT Self Regulating Trace Heating Cable
Quick Find: 1483
Part Code: 790842-000
|Range||Pentair Raychem KTV Self Regulating Heating Cable|
Electrical heat-tracing for process temperature maintenance applications up to 150°C which may be subject to steam cleaning.
The KTV family of self-regulating, parallel circuit heating cables is used for process temperature maintenance of pipes and vessels.
It can also be used for frost protection of large pipes and for applications requiring high temperature exposure capability.
- Hazardous, Zone 1, Zone 2(Gas), Zone 21, Zone 22 (Dust)
Traced Surface Type:
- Carbon Steel
- Stainless Steel
- Painted or Unpainted Metal
- Organics and corrosives
The KTV heating cables are approved for use in hazardous areas by PTB and Baseefa Ltd.
- PTB 09 ATEX 1117 X & Baseefa06ATEX0186X
- II 2G Ex e II 226°C (T2) & II 2D Ex tD A21 IP66 T226°C
- IECEx PTB 09.0058X & IECEx BAS 06.0046X
- Ex e II 226°C (T2) & Ex tD A21 IP66 T226°C
Maximum Circuit Length
Based on Type 'C' Circuit Breakers According to EN 60898
|Electrical Protection Sizing||Start Up Temperature||Maximum Heating Cable length per circuit(M)|
The above numbers are for circuit length estimation only. For more detailed information please use the Pentair TraceCalc software or contact your local Pentair representative. Pentair requires the use of a 30 mA residual current device to provide maximum safety and protection from ﬁre.
Where design results in higher leakage current, the preferred trip level for adjustable devices is 30 mA above any inherent capacitive leakage characteristic of the heater as speciﬁed by the trace heater supplier or alternatively, the next common available trip level for non adjustable devices, with a maximum of 300 mA. All safety aspects need to be proven.
|Maximum maintain or continuous exposure temperature (power on)||150 °C|
|Minimum bend radius||At -60°C: 51 mm|
|Minimum bend radius||At 20°C: 26 mm|
|Minimum installation temperature||-60 °C|
|Temperature Classification||T2 in accordance with European Standard EN 60079-30-1 5.1.13|
Frequently asked questions
Yes, when using trace heating on plastic pipes ensure that ATE- 180 aluminium tape is used to help disperse the heat around the pipe.
Yes, utilising our in-house design facilities, we can design your complete trace heating requirement.
If the surface area of the pump is substantially greater than that of the adjoining pipework then extra heating cable may need to be considered (depending on wattage of cable installed). Pumps and ...
Most applications can simply be straight traced, reducing costs of materials and installation time without compromising on operational requirements.
Yes, thermal insulation is required on all heat trace applications. Without insulation, surface heat losses can increase approximately 4-5 times.
Generally, no maintenance of our trace heating systems is required but it is recommended that the system is checked for operational and electrical integrity periodically or prior to the winter or p...
Full termination instructions are provided with all our heating tapes
System checks depend on the system installed, constant wattage systems can be fully checked for insulation resistance and continuity. Self regulating systems can only be checked for insulation resi...
When water pipes are exposed to cold temperatures either outdoors, underground or in small spaces, you can protect them from freezing by wrapping them with heat tape. Heating tape is actually a cor...
This is used for a pipe freeze protection application. Electric heat tracing, heat tape or surface heating, is a system used to maintain or raise the temperature of pipes and vessels. Trace heat...
Look for similar items by category
- Trace Heating ProductsSelf Regulating Trace Heating CableKTV Self Regulating Heating Cable
- Trace Heating SectorsIndustrial ApplicationsHeating CablesKTV Self Regulating Heating Cable