Raychem 15KTV2-CT Self Regulating Trace Heating Cable
Electrical heat-tracing for process temperature maintenance applications up to 150°C which may be subject to steam cleaning.
The nVent RAYCHEM KTV family of self-regulating, parallel circuit heating cables is used for process temperature maintenance of pipes and vessels.
It can also be used for frost protection of large pipes and for applications requiring high temperature exposure capability.
- Hazardous, Zone 1, Zone 2(Gas), Zone 21, Zone 22 (Dust)
Traced Surface Type:
- Carbon Steel
- Stainless Steel
- Painted or Unpainted Metal
- Organics and corrosives
The KTV heating cables are approved for use in hazardous areas by PTB and Baseefa Ltd.
- PTB 09 ATEX 1117 X & Baseefa06ATEX0186X
- II 2G Ex e II 226°C (T2) & II 2D Ex tD A21 IP66 T226°C
- IECEx PTB 09.0058X & IECEx BAS 06.0046X
- Ex e II 226°C (T2) & Ex tD A21 IP66 T226°C
Maximum Circuit Length
Based on Type 'C' Circuit Breakers According to EN 60898
|Electrical Protection Sizing||Start Up Temperature||Maximum Heating Cable length per circuit(M)|
The above numbers are for circuit length estimation only. For more detailed information please use the Pentair TraceCalc software or contact your local Pentair representative. Pentair requires the use of a 30 mA residual current device to provide maximum safety and protection from Ã¯Â¬Âre.
Where design results in higher leakage current, the preferred trip level for adjustable devices is 30 mA above any inherent capacitive leakage characteristic of the heater as speciÃ¯Â¬Âed by the trace heater supplier or alternatively, the next common available trip level for non adjustable devices, with a maximum of 300 mA. All safety aspects need to be proven.
|Max Exposure Temp||150 °C|
|Maximum maintain or continuous exposure temperature (power on)||150 °C|
|Minimum bend radius||At 20°C: 26 mm|
|Minimum installation temperature||-60 °C|
|Nominal Power Output||47 W/m @ 10 °C|
|Temperature Classification||T2 in accordance with European Standard EN 60079-30-1 5.1.13|